When you had the full backup I'm assuming sewage was in basement and plumber cleared a main line blockage?
Lots of wrong in one photo. I'm assuming it wasn't a real plumber who installed your bathroom - 180 degrees of change on your trap arm before your vent is not allowed **edit** I see now you say he moved it. - You cannot use a wye when connecting a trap arm to a vent - you cannot wet vent a toilet off 1 1/2 pipe, or an air admittance valve. The toilet in the basement is bubbling because when you flush upstairs, there's no vent to absorb the sudden positive pressure in the drainage system, air will escape through where ever it can...in your case, the lower level toilet. This will also prevent your system from draining properly, leaving you more susceptible to blockages.
LOL LOL>>>>HEY, i think that remer9 guy needs in on this thread Sorry Steve, guy yesterday was trying to wind up where you are now would not listen to anyone.....
Drain pipe problems and plumbing disasters in Sacramento are never simple; corrosion, soil shifting
When excavating or trenching is not considered to be a practical method of installing underground p
The summer is widely considered one the most popular seasons in which to upgrade your home. With th
Copyright 2011 Buffalo Plumbing Showroom | Web Design by Block Club Creative
Although most people don?t associate California with freezing cold temperatures, it isn?t safe to
Victor Perkins is a Mass Communications graduate and an ardent blogger. He has sound knowledge ove
3/8 in. x 1/2 in. Plastic O.D. x MIP AdapterBrand :- Other Price :- $4.98
4 in. x 8 ft. Polypropylene Perforated PipeBrand :- FLEX-Drain Price :- $5.97
1/4 in. x 1/4 in. Plastic Straight ValveBrand :- Other Price :- $11.84
2 in. x 1-1/2 in. x 1-1/2 in. ABS DWV All-Hub Double Fixture Sanitary TeeBrand :- Other Price :- $11.96