When you had the full backup I'm assuming sewage was in basement and plumber cleared a main line blockage?
Lots of wrong in one photo. I'm assuming it wasn't a real plumber who installed your bathroom - 180 degrees of change on your trap arm before your vent is not allowed **edit** I see now you say he moved it. - You cannot use a wye when connecting a trap arm to a vent - you cannot wet vent a toilet off 1 1/2 pipe, or an air admittance valve. The toilet in the basement is bubbling because when you flush upstairs, there's no vent to absorb the sudden positive pressure in the drainage system, air will escape through where ever it can...in your case, the lower level toilet. This will also prevent your system from draining properly, leaving you more susceptible to blockages.
LOL LOL>>>>HEY, i think that remer9 guy needs in on this thread Sorry Steve, guy yesterday was trying to wind up where you are now would not listen to anyone.....
Leaky, damaged or burst pipes are probably not on your list of favorite tasts to tend to. Whether t
Benefits of Trenchless Sewer Repair You Need to Know Every single drain in your plumbing system is
It?s that time of the year again? Families and friends come together, share meals, celebrations and
People today are more concerned than ever about contaminants in the water that enters their homes.
Maybe you?ve heard of the ?Giving Pledge,? in which Warren Buffett, Bill Gates and a bunch of othe
We?re well adjusted to our school year routines and October is already calling. Why not make some t
3 in. x 3 in. PVC DWV 90-Degree Mechanical ElbowBrand :- Other Price :- $12.56
2 in. x 2 in. x 1-1/2 in. ABS DWV H x H x H WyeBrand :- Other Price :- $4.76
1-1/2 in. Steel FlangeBrand :- Everbilt Price :- $3.59
1/2 in. x 3/8 in. Brass 90-Degree Push-to-Connect x MNPT Dishwasher ElbowBrand :- SharkBite Price :- $7.87